Payment & Shipping Terms:
|Starting Mode:||Multiple Starting Modes||Stop Mode:||Multiple Stop Modes|
|Power Frequency:||50Hz||Starting Torque:||High Starting Torque|
scr soft starter,
thyristor soft starter
Heavy Load Ball Crusher Three Phase AC220V-690V 22KW High Torque Asynchronous Electric Motor Thyristor Soft Starter
Heavy Load Ball Crusher Three Phase AC220V-690V 22KW Squirrel-Cage Asynchronous Electric Motor Thyristor Soft Starter is a new type motor starting and protection device that is integrated with power electronic technology, microprocessor and automatic control. This soft starter is able to steadily start and stop motor without step change so as to avoid mechanical or electric impact resulted from using conventional starting modes such as direct starting, star-delta starting and auto voltage reducing starting, and effectively reduce starting current and distribution capacity for fear of more investment on capacity expansion.
|Terminal No.||Name of terminal||Description|
|Main circuit||1L1, 3L2, 5L3||AC power input terminal||
Three-phase AC power supply
|2T1, 4T2, 6T3||Soft start output terminal||Asynchronous motor|
|Control circuit||X1/1||Current sampling||Transformer ratio/5A|
|X1/4||RUN||Start when X1/4 and X1/3 are short circuited|
|X1/5||STOP||Stop when X1/5 and X1/3 break|
|X1/6||Bypass output relay (K11, K12)||K11-K12 close when output is available and contact capacity AC250V/5A, DC30V/5A|
|X1/8||Fault output relay (K21, K22)||K21-K22 close when output is available and contact capacity AC250V/5A, DC30V/5A|
|X1/11||L||Control power (220VAC)||AC110V--AC220V±15% 50/60Hz|
Conditions Of Usage
|Control Power||AC110V--AC220V±15% 50/60Hz|
|Adaptive Motor||Squirrel-cage three-phase asynchronous motor|
|Start Mode||1) Current-limiting start;
2) Voltage ramp start;
3) Current ramp start;
|Stop Mode||1,Soft Stop; 2,Free Stop;|
|Starting Times||It is recommended not to exceed 10 times per hour.|
|Protective Function||1, Over-heat protection for soft starter;
2, Protection for too long starting time;
3, Input open phase protection;
4, Output open phase protection;
5, Phase error protection;
|Cooling Pattern||Natural wind cooling|
|Place to be used||Indoor location with good ventilation free from corrosive gas and conductive dust.|
|Enviroment Condition||Below 2000M. It have to rise the rate power when the altitude is more than 2000M.
Ambient Temperature -25+45°C
Ambient Humidity 95%(20°C±5°C)
Dust: If too much dust, it will reduce the insulation level of the soft starter, even causes the soft starter does not work.
Brush the dust with clean and dry brush.
Remove dust with compressed air machine.
2. Condensation: If condensation, it will reduce the insulation level of soft starter, even causes the soft starter does not work.
(1) Blow it with a hair dryer or electric stove.
(2) Bring it to power distribution room for dehumidification.
3. Regularly check components' intact. Whether it can work properly.
4. Check soft starter' cooling channel, ensure they are not clogged by dirt and dust.
Before maintenance checking, it has to cut off all power in the line side of soft starter.
Contact Person: Sales Manager